Fault Current Limiters (FCLs) act as an additional high impedance to limit high fault currents to an acceptable level. In normal operation, FCLs have almost no impedance and are "invisible" to the system. Unlike fuses or disconnectors, FCLs do not completely disconnect in fault case. After the fault current disappears, they can return to normal operation. Due to their very short reaction time, FCLs can act and reduce the short circuit current so that the circuit breaker can act in their nominal performance range, if needed. Typically, FCLs are used in low and medium voltage levels.
FCL can be classified in two major types, which can further be subcategorized per technology:
Components & enablers
Advantages & field of application
By installing FCLs, system operators or commercial customers can optimise the system by application of standard solutions with specific (low) nominal short circuit currents. Major advantages include:
- Reduction of the short-circuit current of the system, allowing the circuit breakers to act in their nominal performance range
- Reduction of voltage sags and flicker due to the lower total source impedance
- Reduction of harmonics due to the lower total
Technology Readiness Level
In case of HV (145 kV and below):
- Non-superconducting FCL : TRL 9
- Super conducting FCL (SFCLs): TRL 3 - TRL 7 depending on technology types and voltage level
In case of HEV (245 kV or more): TRL 3
Research & Development
Current fields of research: Superconducting materials, compactness, self-triggering, increasing maximum voltage level, time to return to normal operation, cost reduction.
Best practice performance
Voltage rating: up to 138 kV
Current rating: up to 6.3 kA
Limiting capability: 210 kA (RMS)
Best practice application
Designing, building and testing of an FCL prototype in Tidd substation of American Electric Power.
A three phase 138 kV, 1300 A saturable iron-core type 2G HTS FCL unit that reduces a 20 kA fault current by 43 % and instantaneously recovers under load was installed on the LV side of a 345 kV/138 kV transformer to protect the feeder.
By employing fault current limiters, the electrical installed equipment is protected.
UK, Newhaven, East Sussex
The Energy Technologies Institute worked on implementing an FCL in a main substation of UK Power Networks to supress damaging currents and provide network capability and reliability.
A novel design was demonstrated that provides a simple, reliable and low maintenance solution and is fully scalable to other voltage levels. The concept of magnetic flux alteration for the iron core saturation is used. Instant, self-triggering response to new faults and quick recovery after clearance without interruption in the network as well as being able to cope with multiple consecutive faults are all benefits of the chosen design.
Shorter connection times and reduced costs of connection with increasing shares of embedded generation. Increased efficiency and flexibility and resilience of the electric network is achieved.
 TU Sofia. Fault Current Limiters – Principles And Application. [Link]
 Cigre. Fault Current Limiters. [Link]
 Asghar, Rafiq. Fault Current Limiters Types, Operations and its limitations. [Link]
 ABB. Is-limiter, an advanced fault current limiter for complex applications. [Link]
 J Electr Eng Technol. Thyristor-Controlled AC Reactor Based Fault Current Limiter for Distribution Network Stability Enhancement. [Link]
 H. Yousefi, M. Mirzaie and F. Aminifar. Reliability assessment of HV substations equipped with fault current limiter considering changes of failure rate of components. [Link]
 F. Moriconi, F. De La Rosa, F. Darmann, A. Nelson and L. Masur.Development and Deployment of Saturated-Core Fault Current Limiters in Distribution and Transmission Substations. [Link]
 Moriconi F, de La Rosa F, Singh A, Chen B et al. An Innovative Compact Saturable-Core HTS Fault Current Limiter – Development, Testing and Application to Transmission Class Networks. [Link]
 Martini L. Superconducting Fault Current Limiter Applications. [Link]
 Innovit. UFCL Ultra Fast Current Limiter. [Link]
 Science Business. GridON’s breakthrough commercial Fault Current Limiter is in service at a UK Power Networks substation. [Link]